2XS(F)K2Y 1x1200RMS/210 76/132 (145)kV
StandardsInternational : IEC 60840
Stranded segmented copper conductor class 2 according to IEC 60228, semi conducting conductor screen, insulation of cross-linked polyethylene (XLPE), semi conducting insulation screen, semi conducting swellable bedding, copper screen, swellable bedding, lead sheath and PE sheath.
Application in ground, outdoors, in tubes, in water, indoors and in cable ducts.
Optionally watertight conductor, construction without copper screen, semiconductive layer on PE sheath, embossed marking or Fiber Optics in screen area for temperature measurement available.
All high voltage cables are manufactured on the basis of specifications and can be adapted to the requirements of the customer. Therefore, all technical information are purely for information purposes and the electrical characteristics are calculated for values which are specified in the data sheets. For your specific requirements and laying arrangements please don't hesitate to contact us.
|Nominal insulation thickness||15.0mm|
|Lead sheath thickness nominal||2.5mm|
|Nominal outer sheath thickness||4.0mm|
|Maximum operating voltage||145kV|
|Max. DC resistance of the conductor at 20°C||0.0151Ohm/km|
|A.C. Conductor resist. 50Hz and at 90 °C||0.0491Ohm/km|
|Nominal phase capacitance||0.272µF / km|
|Charging current max.||6.5A/km|
|Maximum electric stress||6.6kV/mm|
|Permissible short circuit current conductor 1s||172kA|
|Permissible short circuit current screen 1s||40.0kA|
|Grounding type||Solid bonding|
|Thermal soil resistivity dry zone||2.5K*m/W|
|Thermal soil resistivity wet zone||1K*m/W|
|Permissible current rating when buried||875A|
|Permissible transmission capacity, buried||200MVA|
|Maximum pulling force by laying||60kN|
|Number of systems||1|
|Laying depth, center of system||1200mm|
|Ambient ground temperature||20°C|
|Minimum installation temperature||-20°C|
|Bending factor when installed||15(xD)|
|Bending factor when laying||30(xD)|
|Longitudinal water tightness||Yes|